in the HPWC charger there are dip switches to configure the charger to know the size of the breaker it's wired to.
Question is related to the 80% rule (40 amp breaker only use 32 amps of continuous load).
Do you set the dip-switches in the HPWC to match the breaker, or the draw?
i.e. if I have a 60 amp breaker - would I set the HPWC dip switches to the 50 amp setting or the 60 amp setting?
Please Login to Comment