My contractor is telling me I need a cutoff between the Jbox (already ran the 60A/240V wiring to the garage) and the 'charger' and that this would cost $600. Anybody else get this response? I was told this is 'code' but I read the Seattle electrical code and could not find the requirement.
I would have thought the cutoff is 'pull the plug out.'
Anybody have an electrical contractor they liked for installing the NEMA 14-50 in Seattle?
Please Login to Comment